cost structure creates a lot of innovation for users.
Create an opportunity to optimize project investment, therefore, it is necessary to start from engineering programming
Think about lowering costs in the first place!
This is what we developed the Freelance 800F system for:
Keeping hardware prices consistent with those of programmable logic controllers
In this way, cost efficiency can be improved by reducing user engineering costs.
How the Freelance 800F process control system helps users reduce
Low engineering cost?
By using a complete engineering tool (Control Builder
F) to configure the entire control system, including automation functions
function, operator interface display and logging, and configuration of the fieldbus.
equipment (PROFIBUS, FOUNDATION Fieldbus,
HART, etc.) and device parameter settings.
Automatic generation of global data between the process control station and the operator station
According to communication.
For field devices, process control stations and operator stations, a unified global database is used for the entire control system, thereby reducing
cost and time investment in establishing data communication and interactive access.
And ensure the consistency of data throughout the system.
Provide system-wide unified inspection of user applications, overriding
from process control stations, operator stations to intelligent field devices, including
Including the integrity and consistency check of the user program.
The programming language strictly complies with the international standard of IEC61131-3, and has
There are high-performance graphics editing functions:
– Function Block Diagram (FBD)
-Ladder Diagram (LD)
– Instruction List (IL)
– Sequence Control Chart (SFC)
. Structured Text (ST)
Extensive function block library, user-defined function blocks can also be added
Added to it, the macro library and graphic symbols can be customized for the user.
Blocks can create graphics and operator panels.
Any standard can be integrated by means of GSD file import
PROFIBUS-DP and PA devices, and through user-defined pairing
dialog box to design the configuration window for these devices.
Profibus field controller can be integrated through FDT/DTM technology
The Freelance 800F process control system is divided into operator levels
and process control level. The operator level contains controls for operation and display.
Archiving and logging, trending and alarming functions. Controller executes open loop
and closed loop control function.
Freelance 800F DigiVis Operator Level
DigiVis operator stations use PC hardware, either standard commercial
Business PCs can also be industrial-grade PCs and run on Micro-
under soft Windows operating system. DigiVis supports dual-screen display operation
operating technology, that is to say, two operations can be performed using one PC
station and operate with a mouse and a keyboard.
Operator level can install one engineering station and several operators
stand. ControlBuilderF engineering station configures and adjusts the system
Mode. Usually, we can use portable devices such as notebooks to
The system is now configured in the office and on site. Operator-level PC
Can also be used as an engineer station. Engineer standing during system uptime
Intervals can be closed without a permanent connection to the system.
Freelance 800F Process Control Stage
At the process control level, the Freelance 800F system can be controlled by
It consists of a number of process control stations connected to I/O units. you can choose this
Some process stations are in redundant mode (CPU redundancy, fieldbus module redundancy
redundant) or non-redundant mode. Modular pluggable input/output modules
Blocks are freely selected and used according to the type and number of system process signals.
AC800F controller connects remote I/O or field device via fieldbus
Communication between operator level and process control level using TCP/IPProject database
All configured signals, variables and process points are in Freelance
800F system’s public database for management.
List of all variables (input, output, internal variables)
Process point list (function block)
Because the database is system-wide. The data only needs to enter a
times, to avoid possible errors caused by multiple configurations.
Project database files can be easily archived or backed up.
When programmed by the user, a list of variables and labels is automatically created.
Moreover, both variables
Protocol system bus (based on Ethernet), you can choose different
transmission medium such as AUI, twisted pair, fiber optic or coaxial cable.
Freelance OPC server for connecting to higher-level operators
station (800xA) or other OPC client. Freelance Control System
Real-time process values and alarms in the system can be accessed via OPC.
We also provide a C language programming interface to embed external
In Windows operating system applications, it is suitable for implementing user
Communicate with non-standard OPC, ie DMS-API software package.